The error types in this file that have not yet been converted are documented here:
There are a variety of messages that indicate errors related to Adapt blocks which will appear in Execute mode. We check that parameters are legal targets for adapt blocks and tell you if illegal ones are used:
Adapt block Module 1,04,31 Block 22325 on drawing 1040379: Adapted block 0 does not exist Adapt block reference does not exist Failed to find target block for adapt block
Impact: If you compile these blocks, you will get no errors. However, when you download and change mode to Execute, the module will go into Error mode (flashing Green status LED) showing one of these error indications:
Solution: Change mode to Configure and correct the error, compile and download again. Of course, take care of all errors of this class first.
Note: Some of these messages can be especially difficult to comprehend. We had clients experiment with an adapt block that was applied to an alarm specification, documented as illegal. Here were the results:
Please contact GMCL for assistance with resolving these messages. We might need to ask for files that cause these messages for analysis.
DBDOC ©1996 - 2018 G. Michaels Consulting Ltd., all rights reserved. Website largely available under the terms of the AGPLv3. Unless noted otherwise the following are products, trademarks, service marks and/or registered trademarks of their owners and/or holders in the U.S. and/or other countries. MediaView, Microsoft, Visual Studio and Windows are owned and/or held by Microsoft Corporation. AutoCAD is a registered trademark of AutoDesk, Inc. MicroStation is a product of Bentley Systems, Inc. 800xA, ABB, INFI 90, and Symphony are owned and/or held by ABB Group. RoviSys Turbo Lite Server is owned and/or held by The RoviSys Company.