Adapt block Module 1,01,02 Block 1001 on drawing 1010200A.CAD: Adapted block 1002 does not exist
This message means that an adapt block is attempting to adapt a block that does not exist.
On-site testing has confirmed that an adapt block continues to adapt its target block / spec, even if it has no input. Since block types cannot be changed, the unintentionally adapted spec is legal, but not likely correct.
As far as we have determined, if you try a cold reload of a block with these specs, the module will not run. You can, however, load the redundant controller and fail over to it with no problem. The error should be fixed to avoid giving you problems when you do not expect them.
In the above image, the adapt block has an S2 value of 1383, however there is no block 1383 on the same module. This means that no adaptation is available. In the below image, spec 2 is a 0, so there is no block for this adapt block to adapt. Therefore this block is doing nothing.
This message is likely to show an error in the system configuration. It should be reviewed. The issue raised may be in unused logic or graphics, or have other realities that make it a non-issue.
Please contact us for help resolving your error messages.
DBDOC ©1996 - 2018 G. Michaels Consulting Ltd., all rights reserved. Website largely available under the terms of the AGPLv3. Unless noted otherwise the following are products, trademarks, service marks and/or registered trademarks of their owners and/or holders in the U.S. and/or other countries. MediaView, Microsoft, Visual Studio and Windows are owned and/or held by Microsoft Corporation. AutoCAD is a registered trademark of AutoDesk, Inc. MicroStation is a product of Bentley Systems, Inc. 800xA, ABB, INFI 90, and Symphony are owned and/or held by ABB Group. RoviSys Turbo Lite Server is owned and/or held by The RoviSys Company.