FC225 Module 1,27,02 Block 1196 is part of a chain controlled by an FC228 FDD block, so S5(=0) must be 1
This FC225 IOC/DOUT is in an FDD chain (FC228). S5 must be 1 for exception reporting to work with older firmware.
The Harmony Function Code Manual says:
From the client informing us of this problem:
Further investigation indicates that the problem affects only the value displayed or fed into subsequent logic. Also, the problem is eliminated (as is the need for S5=1) if the BRC firmware is level M5 or above and the Gateway (S800 IO FC 227) is at least G5. If this is the case, there is no problem. ABB Case ABB20161007E0252 covers the details. It is not known if ABB clients were directly informed of this problem.
If the firmware revisions are not as indicated, the problem can exist.
This message is likely to show an error in the system configuration. It should be reviewed. The issue raised may be in unused logic or graphics, or have other realities that make it a non-issue.
Please contact us for help resolving your error messages.
DBDOC ©1996 - 2018 G. Michaels Consulting Ltd., all rights reserved. Website largely available under the terms of the AGPLv3. Unless noted otherwise the following are products, trademarks, service marks and/or registered trademarks of their owners and/or holders in the U.S. and/or other countries. MediaView, Microsoft, Visual Studio and Windows are owned and/or held by Microsoft Corporation. AutoCAD is a registered trademark of AutoDesk, Inc. MicroStation is a product of Bentley Systems, Inc. 800xA, ABB, INFI 90, and Symphony are owned and/or held by ABB Group. RoviSys Turbo Lite Server is owned and/or held by The RoviSys Company.