Station Module 1,01,02 Block 1001 span 20.0 [S10] and APID Module 1,01,02 Block 1501 gain 6.5 [S11] product 130.0 is greater than 125.0
The overall gain constant of a PID (FC 18 or 19) or APID (FC 156) controller is designed to scale PV / SP values into a range of 100%. When this is done, the proportional gain constant, in particular, is 1.0 for a gain of one control algorithm.
These messages show where that situation does not exist. These blocks can be tuned, but the tuning constants will not be "normalized" and thus will be subject to misinterpretation.
The product of S11 on the APID and the S10 on the M/A MFC/P must fall in the range of 80 to 125. This error occurs when the product is below that range.
This message reports system information that is otherwise difficult or impossible to find.
Please contact us for help resolving your error messages.
DBDOC ©1996 - 2018 G. Michaels Consulting Ltd., all rights reserved. Website largely available under the terms of the AGPLv3. Unless noted otherwise the following are products, trademarks, service marks and/or registered trademarks of their owners and/or holders in the U.S. and/or other countries. MediaView, Microsoft, Visual Studio and Windows are owned and/or held by Microsoft Corporation. AutoCAD is a registered trademark of AutoDesk, Inc. MicroStation is a product of Bentley Systems, Inc. 800xA, ABB, INFI 90, and Symphony are owned and/or held by ABB Group. RoviSys Turbo Lite Server is owned and/or held by The RoviSys Company.