Enhanced Trend: Module 1,01,02 Block 1001 S1 is wired from FC 30 Module 1,01,02 Block 1002 but S2 1 specifies FC 45
The indicated enhanced input is not a supported type. The documentation indicates that this is a configuration error.
From the documentation for ETREND: Enhanced Trend [FC179]:
S2 (Input block type) Identifies type of input to be trended.
The block addressed in S1 must match the input block type in S2 or a configuration error will result.
Enhanced Trend: Module 1,01,02 Block 1136 S1 is wired from FC 68 Module 1,01,02 Block 5131 but S2 0 specifies FC 30
In this case, S1 is coming from the wrong type of block or S2 should be 3.
This message is likely to show an error in the system configuration. It should be reviewed. The issue raised may be in unused logic or graphics, or have other realities that make it a non-issue.
Please contact us for help resolving your error messages.
DBDOC ©1996 - 2023 G. Michaels Consulting Ltd., all rights reserved. All other trademarks and registered trademarks are the property of their respective holders. Website source largely available under the terms of the AGPLv3.